Design and Test and Engineering LabEngineer a test and development lab solution for Datacenter.The labs hardware will consist of:1. HP C7000 Blade enclosure2. NetApp 20503. KVMSoftware requirements:1. Windows 2008 Ent R22. VMWAre View Horizon3. ESX4. VMWare vCenterAir conditioning (AC)Research will need to include a Visio Diagram of rack of rack elevation and specific power and coolant requirements and specifics for all items belowSystem is room-specific and humidity controlledIndependent, not connected to main building systemWith design criteria of 72??F (+/- 2??F) and 45% RH (+/- 5%) as measured at the return air of the AC unitUnit is at least 4 feet from computer rack system, so that condensation or other leaks don?t harm computer equipment, and access for maintenance is possibleUnit uses the campus chilled water system, if available. Design criteria: Entering water temperature at 46??F and return at 60??F.Future planningSufficient redundancy installed:Backup refrigerant-based cooling systems in parallel with the building chilled water systemMultiple AC units in an N+1 designSufficient future expandability and scalability analyzed and designed in conjunction with the mechanical and electrical systemsShutdown capability of automatic systems based on return air temperature monitorStatistics calculated during the design phase of how fast room temperature will rise during a loss of coolingAppropriate plan for removal of water from AC condensation, either by gravity or pumpElectrical systemsCapacity and qualitySeparate, dedicated power panels for the computer equipment and HVAC. Design systems so that ultimate buildout does not exceed 300 watts per square foot.Power quality considerations to determine need for isolation transformers and uninterruptible power supply (UPS) systemsNo heat-generating support equipment in the spacePower Distribution Unit layout with power monitoring and UPS per rackElectrical system with an isolated ground, dedicated neutral, and a grounding gridEmergency planningEmergency/ back-up power not tied into the building life safety systemSeparate back-up power, if desired (for example, UPS- or generator-supplied and maintained by the department)Electrical distribution system with shunt trip for emergency shutdown!
Unlike most other websites we deliver what we promise;
- Our Support Staff are online 24/7
- Our Writers are available 24/7
- Most Urgent order is delivered with 6 Hrs
- 100% Original Assignment Plagiarism report can be sent to you upon request.
GET 15 % DISCOUNT TODAY use the discount code PAPER15 at the order form.